The relay coil is wired between contacts 2 and 5, while the normally closed contacts are wired between contacts 1 and 2.
Each relay or load in the control system has a VA rating. In Figure 3, you will notice the run and start capacitors are wired in parallel to one another, yet both are in series with the start winding.Contactors Explained and Tested: Wiring, Troubleshooting, Problems, Ratings, and Visual Power Up!
If possible, for the given usage you want, I would narrow it to zero so if you set the set point for 70 then the thermostat contacts will close at 70 and turn the heat on. There are several methods of checking a set of contacts to determine they are burned or pitted enough to warrant changing the device.
The other side will only have voltage when the contactor is engaged and working. Notify me of follow-up comments by email. Submit a Comment Cancel reply Your email address will not be published.
You want the delay on start to allow the heat exchanger to heat up and a delay when the thermostat satisfies to dissipate heat in the exchanger.
The potential relay consists of a very high-resistance coil and a set of normally closed contacts. Mechanical Linkage The mechanical linkage of a contactor or relay can cause malfunctions in many different forms, such as sticking contacts, contacts that will not close due to excess friction, contacts that do not make good direct contact, and misalignment of contacts.
In this case, the start capacitor would never be taken out of the circuit, a rumbling sound would be heard, and high amp draws would open motor-protective devices.
Your email address will not be published.
Their function is to assist in starting the electric motor. Often the relay contacts could be stuck or arced in the closed position. Relays and contactors are used in HVAC control circuits to turn things on and off such as blower motor , condenser fan motor or a compressor. They are both normally controlled by 24 volts and they typically pass line voltage to a motor or compressor. Please assume the reader has understanding about sources, loads, switches, relays, contactors, transformers and etc.
Hopefully that helps you enough to complete the task successfully. I turned off air for 4 hrs the other day to fumigate spiders in bacement and when I was done I turned back on. A coil of a contactor or relay should be checked for opens, shorts, or a measur-able resistance.
If a relay or contactor needs to be replaced it needs to be replaced with an exact match relay or contactor. The run and start capacitors are wired in parallel to one another, yet both are in series with the start winding.
However, most re-lays are sealed and inspection is impossible. Some control transformers are multi-tap transformers that can be used on either 120V or 240V to step down the voltage to 24 volts. Also always check the voltage from the transformer for the correct voltage.
In that case I would advise against using the auto feature as it would be possible for you to run the condenser and the gas furnace at the same time.